The Bora radiator is a tastefully stylised Redeco radiator. The simplicity and elegance in a minimalist style. Made of rectangular parallel profiles connected to each other. This is a great example of a modern solution combining both functionality and high aesthetic level. The radiator is available in a wide range of RAL and Radeco structural palette colours. A large heating surface ensures high power of the radiator.
The above main picture shows the radiator in the following version:
- Valve: Duoplex chrome
- Colour: Wenus 3
|model||Surface||Height H||Width S||Weight||Length L||Volume||Power[W]|
|BORA 1 12 elem||2,76||1800||330||36,0||50||8,4||2010||1610||870|
|BORA 1 15 elem||3,45||1800||418||45||50||10,2||2545||1990||1005|
|BORA 1 18 elem||4014||1800||502||54||50||12,3||3000||2350||1185|
|BORA 2 24 elem||5,51||1800||670||72,0||50||20,3||3820||3060||1650|
|BORA 3 12 elem||1,83||1200||330||24,0||50||5,7||1350||1080||580|
|BORA 4 24 elem||3,67||1200||670||48,0||50||10,8||2570||2060||1110|
|BORA 5 12 elem||0,92||600||330||12,0||50||2,9||760||610||330|
|BORA 6 24 elem||1,84||600||670||24,0||50||5,6||1440||1150||620|
Thermostatic valves are not delivered with the radiator.
WK hangers available in RAL and Redeco structural palette colours can be purchased.
Permissible operating parameters:
- max water pressure: 1.0 Mpa
- max water temperature: 95°C
Radiators can be used in low temperature water heating plants of an open system meeting the requirements of PN-091/B-02413 or close system plants meeting the requirements of PN-091/B-02414, in which materials having contact with water and the quality of water comply with the requirements of PN-93/C-04607.
Steel radiators are intended to be used only in a central heating system.
Radiators should be installed in utility rooms without contact with a caustic environment.
Radiators are equipped with two 1/2” diameter connection pipes. Each radiator is equipped with a cap, vent and a set of fasteners. Arrangement of the radiator in the room should correspond to the central heating system design. It is recommended to install the radiator at the lowest level possible while maintaining its function of a dryer, however, at least 100 mm from the floor.
There are no specific requirements for radiators with standard (powdered paint) coatings. It is not acceptable to clean the radiators with abrasive pastes and preparations, etc. Particular care should be exercised when cleaning patina or brass coatings due to its layer of varnish protecting the brass from oxidation.
Water and mild detergents are recommended for care.
It is absolutely not allowed to use aggressive liquids intended for cleaning washing facilities, petrol, solvents, etc.