To make the Alplast range of products more appealing to our customers, we have designed an alternative version of the Tubo radiator which is Tubo Ka. Steel pipes have been replaced by square profiles, giving the radiator a more geometric shape. Fasteners and hangers of the radiator are consistent with the whole design aesthetics and they are square-shaped either. The soaring design of the radiator is highlighted with two central components being moved upwards. The Tubo Ka decorative radiator sets new radiator design trends. It is available in two versions: as a chrome or painted radiator. Its slim structure will fill all narrow spaces of the bathroom, hall or living room.
The above main picture shows the radiator in the following version:
- WDK square welded hanger
- Valve: Exclusive chrome set
- Colour: Saturn 3
|model||Surface||Height H||Width S||Weight||Length L||Volume||Power [W]|
|TUBO 1K COLOUR||0,69||1620||285||8,9||255||4,9||475||380||205|
|TUBO 2K COLOUR||
|TUBO 3K COLOUR||1,39||1620||625||17,5||595||9,8||895||715||385|
Thermostatic valves are not delivered with the radiator.
WDK welded hangers are included.
Permissible operating parameters:
- max water pressure: 1.0 Mpa
- max water temperature: 95°C
Radiators can be used in low temperature water heating plants of an open system meeting the requirements of PN-091/B-02413 or close system plants meeting the requirements of PN-091/B-02414, in which materials having contact with water and the quality of water comply with the requirements of PN-93/C-04607.
Steel radiators are intended to be used only in a central heating system.
Radiators should be installed in utility rooms without contact with a caustic environment.
Radiators are equipped with two 1/2” diameter connection pipes. Each radiator is equipped with a cap, vent and a set of fasteners. Arrangement of the radiator in the room should correspond to the central heating system design. It is recommended to install the radiator at the lowest level possible while maintaining its function of a dryer, however, at least 100 mm from the floor.
There are no specific requirements for radiators with standard (powdered paint) coatings. It is not acceptable to clean the radiators with abrasive pastes and preparations, etc. Particular care should be exercised when cleaning patina or brass coatings due to its layer of varnish protecting the brass from oxidation.
Water and mild detergents are recommended for care.
It is absolutely not allowed to use aggressive liquids intended for cleaning washing facilities, petrol, solvents, etc.